교실 및 기타 학교 공간은 악취와 오염 물질을 없애기 위해 필히 공기가 잘 통해야 합니다.
A typical classroom using a dedicated outdoor air system (DOAS) distributes outside air (OA) to the rooms through a dedicated diffuser or introduced through the return air duct of the sensible cooling system.
To absorb internal latent loads properly designers must design the DOAS to deliver air at a lower dew point than the required dew point condition. The dry supply air will help absorb additional internal moisture, keeping the space at desired dew point conditions and preventing moisture-related problems.
Typically, engineers wanting to use a DOAS best design practice (divide and conquer), would plan to use a system that would deliver OA at a "neutral" condition, 75°F/24°C and 55°F/13°C dew point. This delivered condition is commonly associated with maintaining 75°F/24°C and 50% RH.
A simple DOAS can accomplish these conditions during the cooling season by processing OA through a cold coil down to a 55°F/13°C saturated condition and then reheating the air back up to 75°F/24°C, ensuring the air be delivered at 55°F/13° dew point. However, introducing OA at a 55°F/13°C dew point will not hold the space at 50% RH. A classroom will generate its own additional moisture from the students, space processes (such as in a lab), and infiltration. Schools that mop or steam clean carpets on a regular basis will introduce an incredible amount of additional moisture to the space. All of this additional moisture must be removed from the space in order to control RH within the recommended 40-60% range. Without this moisture control, structural damage and occupant health risks can happen.
Desiccant Dehumidification System DDS
단독제품으로 사용가능하며 고개의 요구사항에 맞게 제작 가능한 제품입니다. 건식 제습로터의 재생을 위해 LNG 가스 직화 방식이…자세히 보기
문터스의 제습기는 에너지 절약형으로 기술혁신을 강화 했습니다. 열교환기가 추가된 모델과 응축기 재열을 이용한 제습방식은 외기도입용…자세히 보기
Primarily designed to be a dedicated outdoor air unit delivering space…자세히 보기
- 모두 표시